Ceiling Recessed Battery Operation LED Frosted Cover Emergency
- Operation: Non-maintained
- Input Voltage: 220-240V 50/60Hz
- Charging Time: more than 24 hours
- Lamp type: 6pcs SMD 5730 LED
- Battery: Ni-cad battery 3.6V1.8Ah
- Indicate: Green LED--AC power on, Red LED--Charging
- Duration time: More than 3 hours
- Construction: Fire-retardant ABS Casing, Plate and Frame; PS
- Size: 265x105x45mm
- Weight: 0.38kg
- Working Temperature: -10℃ to 55℃
1 Set in 1 Inner Box,50Sets in 1 Outer Carton
Outer Carton Size
Ceiling Recessed Mounted
- Use the scissors to cut the trepanning mould on inner box and make
- Open the product and assemble.(Same as above steps 1-5 of L116N-A,
then assemble the frame)
- Put the spring on product.
- Put the product on the wall.
- Connect the AC power.
This product use electronic switch, when connect with AC power,
green led indicator work, and red indicator show recharging. When
power off, lamp bright, two indicators not work.
- Before installation, cut off the AC power.
- Don’t installation this product in outer door, moist and corrosive
gas environment .
- Use single circuit, do not connect with other lights, to make sure
emergency normal recharging.
- Regular checking to make sure working condition is correct.
- When left factory ,the product is discharging, when using pls.
recharging in 24 hours, to meet the rated duration time.
- When long-term storage or out of service, pls. discharge one time
for each three months to keep battery’s performance.